description: The water softener was part of a large industrial water treatment plant without own control.
Consisting of steel pressure vessel / membrane degassing / frame with piping / and valves.
The softening is followed by a membrane degassing, which separates carbon dioxide from the water by means of a hydrophobic membrane with an air flow
Year of manufacture:
(Accessories for the water softening system)
1 (Steel pressure vessel coated with polyethylene)
33 / 250 l (Support gravel 2-3mm / exchange resin)
6 bar ()
35 °C ()
550 mm (pressure vessel)
1 (Bag filter / fine filter type EF-2/10 μm)
PVC (filter housing)
1 (Diaphragm degasser made of plastic)
(The membrane degassing consists of a pressure housing in which a hollow fiber membrane module is installed)
1 (Compressed air valve terminal mounted on the frame to supply the compressed air operated diaphragm valves)
(The system was already operated on an upstream reverse osmosis, and controlled by a central control cabinet at a water treatment plant)